CMM-10/15 mobile oil plant
The unit is built as a self-contained unit with all components and operating assemblies protected by metal panels and easy opening gas-spring loaded doors on the sides and back of the unit. The “Containerized”unit is placed on a tandem axle trailer that is street legal and ready to be towed to any remote location.
The unit consists of a vacuum1Vacuum is space devoid of matter. An approximation to such vacuum is a region with a gaseous pressure much less than atmospheric pressure. chamber, input and output oil pumps, coarse and fine filters2Filter is a device which separates solids from fluids (liquids or gases) by adding a medium through which only the fluid can pass., oil trap, oil heater3Oil heating is used for treatment of oil in degassing, drying and regeneration machines to accelerate the process. Dehydration is based on the difference of water and oil boiling points. Since water boiling point is lower, heating can evaporate that water from the oil before the boiling point of oil is achieved., pipelines with valves, vacuum pump4A vacuum pump is a device that removes gas molecules from a sealed volume in order to leave behind a partial vacuum. section and a control cabinet.
|Capacity, m3/hour / gals. per hour:|
|Processed oil parameters*:|
|Oil output temperature in heating mode, ºС/ ºF||90/194|
|Outlet pressure, MPa||0.4|
|Oil heater power, kW||180|
|Max power consumption, kW||210|
|Residual pressure in vacuum chamber during degassing, mbar, max||267|
|Residual pressure in vacuum chamber during air tightness test, mbar, max||26.7|
|Air leak into the chamber in 1 hour, mbar max:||267|
|Electric power parameters|
|Dimensions, mm/ft, max|
|Weight, kg/lbs, max||3500/7735|
Note: * initial oil parameters:
- volumetric gas content – below 5%;
- mass moisture content – below 01% (100 g/ton);
- temperature – above 0 ºС/ 32 ºF.
**All equipment sold in the USA is designed to operate on 60 Hz AC Power
- transformer oil dielectric strength increase to at least 70 kV;
- transformer drying with simultaneous oil processing;
- initial filling of electrical equipment with insulation oil;
- evacuation of transformers and other electrical equipment;
- simple operation and servicing.